Main range of productEasypact CVS100...250 rangeEasyPact product nameEasyPact CVS device short nameCVS100NA product or component typeSwitch disconnector device applicationDistribution poles description3P network typeAC [Ie] rated operational current100 A AC-22A : AC 50/60 Hz 380/415 V100 A AC-22A : AC 50/60 Hz 440 V100 A AC-23A : AC 50/60 Hz 380/415 V100 A AC-23A : AC 50/60 Hz 440 V100 A AC-22A : AC 50/60 Hz 220/240 V100 A AC-23A : AC 50/60 Hz 220/240 V [Ith] conventional free air thermal current100 A ( 50 °C ) [Icm] rated short-circuit making capacity75 kA with upstream protection circuit breaker2.6 kA switch-disconnector alone breaking capacity codeNA suitability for isolationYes conforming to EN 60947-3Yes conforming to IEC 60947-3 utilisation categoryAC-22AAC-23A earth-leakage protectionWithout Complementary network frequency50/60 Hz control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront [Icw] rated short-time withstand current0.69 kA ( 20 s ) conforming to IEC 60947-31.8 kA ( 1 s ) conforming to IEC 60947-31.8 kA ( 3 s ) conforming to IEC 60947-3 contact position indicatorYes visible breakNo mechanical durability30000 cycles conforming to IEC 60947-3 electrical durability8000 cycles conforming to IEC 60947-3 415 V In AC 50/60 Hz AC-22A :8000 cycles conforming to IEC 60947-3 415 V In AC 50/60 Hz AC-23A : connection pitch35 mm height161 mm width105 mm depth86 mm product weight2.05 kg Environment standardsEN 60947-3IEC 60947-3 product certificationsGOSTIEC electrical shock protection classClass II pollution degree3 conforming to IEC 60664-1 ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsProduct environmentalSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.