Main range of productEasypact CVS100...250 rangeEasyPact product nameEasyPact CVS device short nameCVS250NA product or component typeSwitch disconnector device applicationDistribution poles description3P network typeAC [Ie] rated operational current250 A AC-22A : AC 50/60 Hz 380/415 V250 A AC-23A : AC 50/60 Hz 380/415 V250 A AC-22A : AC 50/60 Hz 220/240 V250 A AC-22A : AC 50/60 Hz 440 V250 A AC-23A : AC 50/60 Hz 220/240 V250 A AC-23A : AC 50/60 Hz 440 V [Ith] conventional free air thermal current250 A ( 50 °C ) [Icm] rated short-circuit making capacity75 kA with upstream protection circuit breaker4.9 kA switch-disconnector alone breaking capacity codeNA suitability for isolationYes conforming to EN 60947-3Yes conforming to IEC 60947-3 utilisation categoryAC-22AAC-23A earth-leakage protectionWithout Complementary network frequency50/60 Hz control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront [Icw] rated short-time withstand current1.35 kA ( 20 s ) conforming to IEC 60947-33.5 kA ( 1 s ) conforming to IEC 60947-33.5 kA ( 3 s ) conforming to IEC 60947-3 contact position indicatorYes visible breakNo mechanical durability20000 cycles conforming to IEC 60947-3 electrical durability6500 cycles conforming to IEC 60947-3 415 V In AC 50/60 Hz AC-22A :6500 cycles conforming to IEC 60947-3 415 V In AC 50/60 Hz AC-23A : connection pitch35 mm height161 mm width105 mm depth86 mm product weight2.4 kg Environment standardsEN 60947-3IEC 60947-3 product certificationsGOSTIEC electrical shock protection classClass II pollution degree3 conforming to IEC 60664-1 ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.