Main range of productEasypact CVS100...250 product or component typeCircuit breaker device short nameCVS250B device applicationDistribution poles description3P protected poles description3d Earth leakage protection (Vigi add on)Without [In] rated current250 A ( 50 °C ) breaking capacity codeB network typeAC [Icu] Breaking capacity40 kA Icu conforming to IEC 60947-2 at 220/240 V AC 50/60 Hz utilisation categoryCategory A trip unit nameTM-D trip unit technologyThermal-magnetic trip unit rating160 A ( 40 °C ) protection typeOverload protection (thermal)Short-circuit protection (magnetic) Complementary network frequency50/60 Hz control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront [Uimp] rated impulse withstand voltage8 kV conforming to EN/IEC 60947-2 [Ics] rated service breaking capacity15 kA conforming to IEC 60947-2 440 V AC 50/60 Hz25 kA conforming to IEC 60947-2 380/415 V AC 50/60 Hz40 kA conforming to IEC 60947-2 220/240 V AC 50/60 Hz mechanical durability20000 cycles electrical durability10000 cycles conforming to IEC 60947-2 415 V In connection pitch35 mm contact position indicatorYes long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.7...1 x In long time delay adjustment typeFixed short-time delay adjustment typeFixed instantaneous pick-up adjustment type IiFixed instantaneous pick-up adjustment range1250 A height161 mm width105 mm depth86 mm Environment electrical shock protection classClass II standardsEN 60947-2IEC 60947-2 product certificationsGOSTIEC ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.